12.2 UST System Operation
12.2.1 Underground Tank System Corrosion Protection Test Summary Documentation
A copy of this document must be maintained at the UST facility that has corrosion protection. This is for both sacrificial anode or impressed current CP systems. There must be no less than three (3) years of CP records.